Hurricane-downgraded-to-Post-tropical storm Sandy has taken out Internap, which operates a global content delivery network and data centers.
Internap has emailed its customers the following warning:
Please be advised that Internap’s LGA11 facility is experiencing significant flooding in the sub-basement of the 75 Broad Street building as a result of Hurricane Sandy. The flooding has submerged and destroyed the site’s diesel pumps and is preventing fuel from being pumped to the generators on the mezzanine level.
The available fuel reserves on the mezzanine level are estimated to support customer loads for approximately 5-7 hours. Once this fuel supply has been exhausted the generator will no longer be able to sustain operation and critical customer power loads will be lost.
According to The Register, a Microsoft employee reported that submarine cables have gone dark. The Service Help Dashboard at Amazon Web Services reported all is well, as did Rackspace.
About the Author: JewishPress.com brings you the latest in Jewish news from around the world. Stay up to date by following up on Facebook and Twitter. Do you have something noteworthy to report? Submit your news story to us here.
If you don't see your comment after publishing it, refresh the page.